Refer the Vigi Installation Guide for the instruction to connect the Vigi module on the Compact NS Moulded Case Circuit Breaker (MCCB).
The M2C programmable contacts are not compatible for installation in Compact NS circuit breaker. For signalization the I/O module can be considered, or the M6C contact with Micrologic P.
Yes, Reflex Tripping is available in all Compact NS/NSX Switch Disconnectors.
The threshold of the Reflex Tripping auto-protection is about 20xIn and time delay is less than 10 ms, as shown in the attached tripping curves.
To obtain the manufacturing date of Compact NS or NSX circuit-breakers, read the screen-printed marking at the top of the front panel.
The code P07351, for example, provides the following information: